8 Channel 0-10V Dimmer Module, 2 Feeds, 120V
Provides eight channels of dimming for 120 Volt residential and commercial lighting applications. Supports 0-10 Volt dimmable fluorescent ballasts and LED drivers. May also be used to switch non-dimmable lighting loads. Installs in a CAEN or CAEN-MLO wall mount automation enclosure as part of a complete Crestron® centralized lighting control system.
Visit the Crestron® Lighting Fixture Compatibility page to find out which Crestron lighting devices have been tested and are compatible with third party lighting fixtures.
The Crestron® CLX-2DIMFLV8 is an eight-channel, two-feed dimmer module designed for 120V lighting system applications. It installs in a CAEN or CAEN-MLO enclosure and provides control of 0-10 Volt dimmable fluorescent ballasts and LED drivers. It can also be used to switch non-dimmable lighting loads. Dual feed capability provides two independent four-channel dimmers in one module space. Each output channel is rated for 16 Amps, with a total module rating of 32 Amps when fed from two separate 20 Amp feeds.
Centralized Lighting Cabinet Installation
Crestron CLX series lighting control modules are designed to be installed in a CAEN or CAEN-MLO wall mount enclosure. Available in a variety of sizes, CAEN and CAEN-MLO enclosures provide a scalable, high-density centralized lighting control solution for any-sized residence or commercial facility. A selection of CLX module types is offered to accommodate a wide range of load types and system configurations.
Termination of high-voltage wiring to the CLX-2DIMFLV8 module is facilitated using a CLT-2DIMFLV8 terminal block, which is sold separately to enable termination of the wiring prior to installing the module. This terminal block mounts beside the module within the enclosure. The 0-10V control wires terminate to the front of the module via detachable terminal blocks. Other low-voltage control signals are bussed between each of the modules within an enclosure via a simple 5-wire link (interconnect jumpers included), which terminates to a single terminal block (model CAEN-BLOCK , sold separately) at the bottom of the enclosure.
The CLX-2DIMFLV8 interfaces with a Crestron control system (a.k.a., control processor or automation processor) via Cresnet. Cresnet is a simple 4-wire network bus that provides the communications backbone for a system of Crestron lighting dimmers, switches, keypads, shades, thermostats, and other devices.
Emergency Lighting Control
The CLX-2DIMFLV8 is UL® 924 and CSA® C22.2 No. 141-15 listed for use in controlling emergency lighting loads. In the event of a power failure, a contact closure from a power loss sensor (Crestron GLS-PLS-120/277 , sold separately) activates the override mode in the CLX-2DIMFLV8 to turn on each designated lighting load if it is off (assuming line power is supplied by a backup power source). The override dimming level can be preset to any value when commissioning the lighting system, so even if the load is already on prior to a power failure, it will change to the preset level when override mode is activated.
- Eight-channel 0-10V dimmer module for residential and commercial lighting applications
- Installs in a Crestron® CAEN or CAEN-MLO enclosure
- Supports 0-10V dimmable fluorescent ballasts and LED drivers
- Also supports on/off switching of non-dimmable lighting loads
- Single or dual feeds — two four-channel dimmers in one module
- Rated 16 Amps per channel, 32 Amps total (using two 20 Amp feeds), at 120 Volts AC
- Customizable dimming curves via software
- Arcless switching
- Built-in air gap relay per channel
- Closure-activated override mode
- UL® 924 and CSA® C22.2 No. 141-15 listed for emergency lighting control
- Crestron system integration via Cresnet®
- Easy termination using a CLT-2DIMFLV8 terminal block (sold separately)
- CEC Title 24 2013 compliant
|Dimmable Load Types
||0-10 Volt fluorescent ballasts or LED drivers (4-wire)
|Switched Load Types
||LED, incandescent, fluorescent, magnetic low-voltage, electronic low-voltage, high-intensity discharge (HID)
|Per Channel Load Rating
|Per Group Load Rating
||Group 1 (Channels 1-4): 16 Amps;
Group 2 (Channels 5-8): 16 Amps
|Module Total Load Rating
||32 Amps 
||120 Volts AC, 50/60 Hz; requires one or two single-phase feeds (may be same or different phases)
||0-10 Volts DC, 100 mA maximum per channel, sink or source
|Via Terminal Block (sold separately)
||LINE 1 – 2: (2) Screw terminals, black, line power feed inputs (per group);
SW 1 – 8: (8) Screw terminals, red, switched load outputs (per channel);
N IN 1 – 2: (2) Screw terminals, white, line power feed neutrals (per group);
N OUT 1 – 8: (8) Screw terminals, white, load neutrals (per channel);
Note: Each terminal accepts one 14-10 AWG wire.
|1 – 8
||(8) 2-pin detachable terminal blocks;
0-10 Volt dimming control outputs;
26 to 12 AWG (0.14 to 2.5 mm²) wire size;
For use with Class 1 or Class 2 wiring
||(2) 5-pin 0.156 inch headers;
Cresnet/Override interconnect ports;
Each connects to the adjacent module using the interconnect jumper provided;
Connects to a CAEN-BLOCK (sold separately) when installed in the lowest position within the enclosure
|Controls & Indicators
||(1) Green LED, indicates line power is applied to the LINE 1 terminal
||(1) Yellow LED, indicates Cresnet communication with the control system
||(1) Pushbutton and (1) red LED for Cresnet setup using TSID (Touch Settable ID)
|1 – 8
||(8) Pushbuttons and (8) red LEDs, each pushbutton toggles the corresponding channel on and off (press and hold to cycle the dimming level up and down), each LED indicates the corresponding load output is energized
||32° to 104° F (0° to 40° C)
||10% to 90% RH (non-condensing)
|Gray metal, surface mount module with (2) integral mounting flanges;
Occupies 1 module space in a CAEN or CAEN-MLO enclosure
||7.53 in (192 mm)
||6.91 in (176 mm)
||3.32 in (85 mm)
|3.15 lb (1.43 kg)
|UL Listed for US & Canada, IC, UL 508, UL 924, CSA C22.2 No. 14, CSA C22.2 No. 141-15, CEC Title 24 2013, FCC Part 15 Class B digital device
to search product certificates.
Please select your region below to see the appropriate Advertised Pricing.